For communication equipment manufacturers, precision electronics manufacturers, computer rooms and other electronic places, electrostatic charge will damage electronic precision instruments, and the sparks generated by electrostatic effect can even lead to fire or explosion. This requires that the ground has anti-static function. The emergence of epoxy anti-static floor paint can solve this problem very well. It can not only eliminate static charge quickly, but also has the advantages of dust-proof, wear-resistant, impact-resistant, compressive, smooth surface and beautiful appearance. Then how should a qualified epoxy anti-static floor paint be constructed? The qualified construction technology of epoxy anti-static floor paint is as follows:
1. Plain treatment
According to the condition of the grass-roots ground, polishing, repairing, decontamination and dust removal are done to make the surface of the ground clean and rough. 基层地面打磨处理
Grass-roots ground grinding treatment2.防静电底漆施工
2. Antistatic Primer Construction
The epoxy antistatic primer is proportionally mixed, stirred evenly, and evenly brushed with a flat knife or drum to enhance the surface adhesion.
Construction of Anti-static Primer3.防静电中涂砂浆施工
3. Construction of anti-static medium-coated mortar
The epoxy anti-static paint is mixed proportionally, and a proper amount of quartz sand is added. It is stirred evenly with a mixer and evenly coated on the ground with batch knives. According to the design, the coating is multichannel, so as to achieve the function of leveling the ground and increasing the thickness of the coating.
Construction of Anti-static Medium-coated Mortar Layer4.防静电中涂腻子施工
4. Putty construction in anti-static
After the anti-static coating mortar layer is completely cured, the epoxy coating is proportionally mixed with appropriate amount of talcum powder, stirred evenly with a mixer, and coated evenly once or twice with a trowel to fill the pinholes in the surface of the mortar coating, so that the ground is completely closed.
Construction of Putty Layer in Antistatic5.无尘打磨
5. Dust-free grinding
After the anti-static putty layer is completely dried, it is entirely polished with a dust-free grinder to completely eliminate knife marks and dust.6.铜箔铺设
6. Copper foil laying
The cumulative static electricity can be effectively eliminated by laying a layer of conductive copper foil in a well-shaped shape and grounding treatment. Laying distance is 2.5m*2.5m, cross-laying.
Paste Conductive Copper Foil7.导电炭黑施工
7. CONDUCTIVE CARBON BLACK CONSTRUCTION
The conductive carbon black is evenly coated on the ground with a drum or trowel.
CONDUCTIVE CARBON BLACK CONSTRUCTION8.防静电面漆施工
8. Construction of Antistatic Topcoat
When the conductive carbon black is completely cured, the anti-static self-flowing flat paint is mixed proportionally, stirred evenly, and coated evenly with a trowel to ensure uniform, flat and no bubbles on the surface.
Anti-static Self-Flow Flat Paint9.养护
Epoxy anti-static floor paint can be used 24 hours after completion of construction, 72 hours after heavy pressure, 5-7 days after maintenance can be put into normal use (25 C, low temperature opening time needs to be extended moderately).
标签:   环氧地坪 环氧地坪漆 环氧地坪施工 地坪 无锡环氧地坪