First of all, attention should be paid to the installation of wall panels in high temperature aging rooms. In the process of splicing, we should pay special attention to the smoothness of the ground. Otherwise, it is easy to have uneven wall panels, which makes it difficult for the roof to fit tightly and lead to large leakage, affecting the internal wind circulation and temperature. When the unevenness of the ground occurs, we need to pay attention to it. Generally, we adjust the size of the rock wool board again to make the upper level, and the roof laying is also convenient. When splicing between wall panels, we also need to pay attention to whether there is a gap between the panels and panels, usually with glass glue, which is beautiful, sealed, and better insulation effect! 高温老化房风道的安装注意事项。风力管道系统符合《通风与空调工程施工质量验收规范》GB50243-2002标准，通常采用循环系统、加热系统和超温排风系统组成。循环系统、超温排风系统、加热系统及配套的风道系统部分循环系统采用循环风机和配套风管进行循环，可保证测试区内温度匀，加热系统采用电热器加热，加热器放置于老化房顶上循环风道中，四周加防火隔热材料。采用PID温度模块控制，温度到达产品所需要温度后根据室内温度波动自动调节加热器功率大小配合保温库板的保温性，使室内温度精确稳定在所设定温度数值可在指定的时间内内将室温加至设定度，当温度升至设定值时加热器停止加热.加热器具有过热保护装置。用低噪音风机排风，循环控温过程：当开机时加热器开始加热 温度到达设定值时加热器停止加热，在老化产品的过程中始终保持循环状态，以保证温度均衡。整套系统动作具有性能稳定，控制精确、温度波动小，均衡度高、噪音小等特点。
Cautions for installation of air duct in high temperature aging room. Wind power pipeline system meets the GB50243-2002 standard of "Acceptance and Acceptance Standard for Construction Quality of Ventilation and Air Conditioning Engineering". It usually consists of circulating system, heating system and over-temperature exhaust system. Circulating system, over-temperature exhaust system, heating system and supporting duct system are partly circulated by circulating fan and supporting duct system, which can ensure uniform temperature in the test area. The heating system is heated by electric heater. The heater is placed in the circulating duct on the aging roof and surrounded by fire-proof and heat-insulating materials. PID temperature module is used to control the temperature. After the temperature reaches the required temperature of the product, the power of the heater is automatically adjusted according to the fluctuation of indoor temperature and the insulation property of the thermal insulation warehouse board, so that the indoor temperature can be accurately stabilized. The temperature can be increased to the setting degree within a specified time. When the temperature rises to the setting value, the heater stops heating. The heater has an overheating protection device. The process of exhausting air with low noise fan and circulating temperature control: When the heater starts to heat when the temperature reaches the set value, the heater stops heating, and keeps the circulating state throughout the aging process to ensure the temperature balance. The whole system has the characteristics of stable performance, precise control, small temperature fluctuation, high equilibrium and low noise.
标签:   环氧地坪 老化房 环氧地坪漆 环氧地坪施工 地坪